Near Barnes Dr, Kansas City 2 years ago
Reason for Replacement
Water Pressure Inside
Replace electric tank. The elements kept throwing the breaker on this tank, the homeowner replaced the elements and the thermostats for this tank and it just threw the breaker again.
After further investigation the inside of the tank had been flaking away and pieces of metal were floating around inside the tank causing the breaker to trip. Installed new 50 gallon Electric water heater along with a new supply line for a fridge. Main shutoff valve was also leaking which was replaced with a new valve. Also repaired a leaking outside faucet by replacing the washer.
Feedback by Customer
Chase provided superior customer service. When working with a water system that is 22 years old, you never know what can happen. Chase was able to overcome every issue without a struggle. He even resolved other minor plumbing issues while on site. Excellent service man!