Near Boehm Dr, Lenexa 1 year ago
Reason for Replacement
Water Pressure Inside
Water Pressure City
Old water heater had quit producing any hot water. The blower would kick on but the pilot would not ignite. There was an error code 7 which means the manifold needs to be replaced. The part was $400 so the tank was replaced. A low spot in the 2" PVC flue may have attributed to the early tank failure.
AO Smith GPVT 40 100 Power Vent water heater installed and supports added to the flue. Flexible lines replaced with copper for both the water and gas.
Feedback by Customer
No Feedback Given