Near W 98th Ter, Lenexa 1 year ago
Worked great for 16yr
Reason for Replacement
Water Pressure Inside
Water Pressure City
The expansion tank on this water heater had been installed only a few years prior and was filled with water. The pressure reducing valve had also failed which caused the water pressure to rise to 89 psi. When an expansion tank is full of water it tends to fail within a year or two.
Pressure Reducing Valve was replaced two saddle valves were removed. The thermal expansion tank was inflated to 75 psi and the water pressure was also set to 75.
Feedback by Customer
Super guy, very knowledgeable