Near NW 62nd Ter, Kansas City 1 year ago
Reason for Replacement
GAS VALVE / PILOT
Water Pressure Inside
Water Pressure City
The Rheem water heater had been going out for the past year after the tank would heat up the pilot would go out. Another plumber came out and replaced the thermocouple but it was most likely the gas valve that was causing the pilot to go out.
Upon arrival it was clear that the old flue for the existing water heater had worn thin and had several holes. The flue pipe was replaced all the way to the double wall section. The water pressure was also high due to a failed PRV. The pressure reducing valve was replaced and a thermal expansion tank was installed.
Feedback by Customer
No Feedback Given