Near S Deer Run St, Olathe 1 year ago
Worked well until it started leaking. Water pressure was inconsistent but worked well for our family of five.
Reason for Replacement
Water Pressure Inside
The old water heater had a very short lifespan for this area. The water pressure was only 40 psi in this house, yet there were obvious signs of thermal expansion. The homeowner also reported having to replace the thermocouple about a year ago which was likely an unrelated issue.
A thermal expansion tank was installed along with the GCR 50 400 from AO Smith.
Feedback by Customer
Chase was very knowledgeable about troubleshooting and ways to fix the problem. He explained everything to me and was kind enough to call my husband at work to give him a summary of issues he was seeing. He was quick, punctual and professional. Would highly recommend!