Near Sagamore Rd, Leawood 1 year ago
Reason for Replacement
Water Pressure Inside
Water Pressure City
Both of these water heaters had a long life despite being under 100 psi of water pressure. This Leawood neighborhood has likely had a pressure increase in the past year or two.
We discussed the needs with the client and decided that they would be better off with only one 50 gallon tank opposed to two separate tanks. Upon installing the new water heater we found a baseball size hole in the backside of the flue that was not visible unless the flue was taken apart. These water heaters were almost certainly dumping Carbon Monoxide inside of this families home. We replaced the entire section of flue and installed a PRV.
Feedback by Customer
No Feedback Given