Near W 81st St, Lenexa 1 year ago
Reason for Replacement
VENTING / INSTALLATION
Water Pressure Inside
Water Pressure City
The existing water heater was installed 10 years prior due to an unsafe flue. This power vent model actually wasn't installed correctly. Too large of a vent was used and the slope went in the wrong direction. This likely attributed to the blower failure within the first 6 years which was covered under warranty, even though it was an installation issue. The second issue was determined to be a bad gas valve. Due to the age, the tank was replaced instead of repaired.
The water pressure was 100 psi due to a failed PRV. The vent for the blower was also replaced with 2" and restrictor plates were used to prevent future problems. The slope for the flue was also redone.
Feedback by Customer
No Feedback Given