Near W 52nd St, Shawnee 1 year ago
Reason for Replacement
GAS VALVE / PILOT
Water Pressure Inside
Water Pressure City
The old water heater was undersized for the home and was turned all the way up. Shortly after turning up the temperature in this 18 year old AO Smith water the pilot went out and they lost hot water.
A new water heater was installed and a thermal expansion tank was installed. The water pressure from WaterOne was 130 psi and the PRV reduced it down to 75. This brings the water pressure in the house up to 130 when the tank is heating water. In this environment a thermal expansion tank is recommended.
Also installed new shutoff valves and replaced the saddle valve.
Feedback by Customer
No Feedback Given