Near N Beaman Ave, Kansas City 1 year ago
It worked great until it rusted through and started leaking. I hope my new one lasts as long.
Reason for Replacement
Water Pressure Inside
Water Pressure City
The old water heater was 22 years old and leaking slowly from the bottom of the tank. The water heater was under 96 lbs of water pressure and was on a closed system. The water pressure was high due to the failed PRV. Other water pressure readings in the neighborhood show that the water pressure was not always that high.
AO Smith water heater installed along with thermal expansion tank and new PRV. The line for the humidifier was also replaced with a full brass body compression valve which was also lead free. The water pressure was set to 75 psi and the expansion tank was also set to 75 psi.
Feedback by Customer
Chase did a great job of explaining what we needed and in replacing our water heater in a timely manner. Thank you!