Near Cottonwood Dr, Shawnee 1 year ago
Reason for Replacement
GAS VALVE / PILOT
Water Pressure Inside
Water Pressure City
This old Bradford White held up pretty well considering the water pressure was about 100 psi. There was no thermal expansion tank and the issue was actually with the gas valve, not a leaking tank.
New PRV installed to reduce water pressure down to 75 psi. AO Smith water heater installed and the saddle valves for the humidifier and fridge were replaced.
Feedback by Customer
No Feedback Given