Near S Widmer St, Olathe 1 year ago
Reason for Replacement
Water Pressure Inside
Water Pressure City
The old Bradford White water heater had been backdrafting for quite some time due to a lack of combustion louvers installed when the basement was finished. This likely attributed to the corrosion on the top of the tank which prompted the replacement.
Flue was redone to increase the ability to draw. The PRV was also replaced and the humidifier valve was replaced with a compression stop.
Feedback by Customer
No Feedback Given