Near N Leeview Dr, Olathe 1 year ago
Reason for Replacement
Water Pressure Inside
Water Pressure City
This tank had multiple issues. The most pressing was a gas leak that was verified by the gas company. It was determined that the gas valve was emitting gas into the house. The tank also seemed to be leaking water as the shell was wet. The gas connector was longer than was was allowed and no drip leg was installed. There may have been a water softener that was installed for the early stages of this water heaters lifecycle.
New AO Smith tank installed and elevated off the basement floor. The water pressure was right at 80 and no PRV was present. The gas line was corrected and a drip leg was added.
Feedback by Customer
No Feedback Given