Near S Earnshaw St, Overland Park 9 months ago
Chase was terrific today. He arrived ahead of schedule and reached out before to let us know he was on his way. I would highly recommend him for any hot water heater and related repairs.
Reason for Replacement
Water Pressure Inside
Water Pressure City
The old water heater was installed as a second tank. The plumber that put it in did not install the correct size flue and backdrafting had occurred. Also neglected to install a thermal expansion tank.
A 5x4x4 vent connector was added and a 4x3x3 Y was added as well as a new flue for both water heaters. A thermal expansion tank was also installed along with a new PRV. The water pressure was 106 psi before the new PRV was installed.
Feedback by Customer
5 stars all around. Chase did an outstanding job replacing our hot water heater. He is very knowledgeable and went above and beyond my expectations. I would highly recommend him to anyone who needs service.