Near Reeds St, Overland Park 9 months ago
My old water heater was leaking and Chase came to replace it.
Reason for Replacement
Water Pressure Inside
A second water heater was added after the home was built. The plumber did not correctly size the flue for the second tank. An additional flue was ran to support the second tank.
New flue ran for second tank and the T was removed. A connector rise was also added to the new installation to prevent any additional backdrafting. The rust on the first tank are an indicator of backdrafting.
Feedback by Customer
Chase was very knowledgeable and was very responsive. He walked through everything about my new water heater installation and how my water heaters were originally installed (and why certain changes needed to be made). He was on time (early even) and very accommodating with my work schedule too.