Near Haskins St, Overland Park 9 months ago
Reason for Replacement
Water Pressure Inside
Water Pressure City
The old water heater had clear signs of backdrafting which was likely caused by a 3" flue where a 4" flue should have been installed.
New high recovery water heater installed along with 4" vent connector and 4" flue. Thermal expansion tank installed along with new ice maker stop and the flex gas line was replaced with iron pipe. A new PRV was also installed and the pressure set to 70 psi as was the expansion tank.
Feedback by Customer
No Feedback Given