Near N Amoret Ave, Kansas City 2 months ago
Reason for Replacement
GAS VALVE / PILOT
Water Pressure Inside
Water Pressure City
The old water heater had an improper venting configuration. The water pressure was also much higher than it was suppose to be. The vent for the water heater went from 6" to 3" which is against code.
The gas line was updated with a new shutoff and drip leg and also hard piped. The vent was replaced to 4" and the old wye from the furnace was removed. There was also a 1' rise off the top of the tank that was added. A new PRV and thermal expansion tank was also installed.
Feedback by Customer
No Feedback Given