Near W 121st St, Overland Park
Reason for Replacement
Water Pressure Inside
Water Pressure City
The old water had a very slow leak from the bottom of the tank after only 10 years. The water pressure was checked and it was 100 psi.
A new PRV was installed to lower the water pressure to 75 psi, thus creating a closed system. A thermal expansion tank was installed on the new water heater. The main shutoff was also replaced as the old valve did not completely shutoff the water.
Feedback by Customer
They called to let me know they where on their way , I appreciated that . I also felt like Chase explained everything and went a above and beyond to do the job right!